Equipment Name: Acid fume Scrubber
Treatment Capacity: set acid fume treatment system, designed capacity is 50,000m3/h ï¼ˆaccording to customer requirement)
Composition The whole system is composed of suction hood, ventilation ducting, acid mist scrubber, blower, chimney, control valve, electrical cabinet, etc.
Set up suction hood overhead the pollution source, the suction hood will generate strong air attraction with force of the blower; the acid mist will be sucked into the ventilation ducting.
Function of the suction hood is to capture the acid mist and generate a strong negative pressure area, forcing the acid mist moving into the suction hood.
Function of the ventilation ducting is to ensure the ventilation of air flow.
Function of the acid mist scrubber: to purify the acid mist.
Function of the blower: the blower is just like the heart of the system, the power source of circulation air flow; the blower is placed behind the scrubber, which will protect the impeller from impact of high-speed and disordered dust particles, improving the service life and reducing the backpressure, ensuring the normal long-term operation.
Function of the circulation water pump: spray alkaline liquid and neutralize acid mist, and make it recycled.
The acid mist will be integrated into the scrubber, and the treated air will be discharged from the chimney via the blower. Each suction hood is equipped with independent air valve for adjusting the air flow; if there is no need to open at the same time, the operator can close it, making the negative pressure of the running suction hood much stronger, more beneficial to the acid mist gathering.
With the dynamic strength of the blower, the dusty acid will go through the suction ducting into the acid fume scrubber. The acid fume will go up the first level spraying section from the bottom of the scrubber. The absorption liquid will spray out from the evenly placed nozzles; the numerous fine fog-drops will contact with the air and have chemical reaction. The air will go up to the packing layer. The turbulence of the small packing balls, with the wind dynamic force, will make the aireous phase lead have chemical mass transfer reaction with the strong alkaline matter in the spray. The reacted substance will flow down to the bottom storage tank. The harmful air which hasnâ€™t been completely absorbed will go up to the second level spraying section. The absorption liquid will spray out from the evenly placed nozzles; the numerous fine fog-drops will contact with the air and continue to have chemical reaction. Just like the first level absorption process, the air will enter into the demister on the top of the scrubber. The absorption liquid contained in the air will be cleared away and the clean air will be discharged into the atmosphere through the exhaust chimney. The absorption liquid can be recycled to be used. The sediment inside the water tank should be removed manually.
Dust Collection Method
The circulation water inside the scrubber should be discharged at regular intervals, the discharged leaded sewage should be discharged to the sewage treatment station